G306032 (B) (EN)
|StandardsBS EN 1364-1,Fire resistance tests for non-loadbearing elements - Walls.||Standard types|
|StandardsBS EN ISO 140-3,Acoustics - Measurement of sound insulation in buildings and of building elements. Laboratory measurement of airborne sound insulation of building elements.||Standard types|
|StandardsBS 5234-2,Specification for performance requirements for strength and robustness including methods of test.||Standard types|
|Retaining channel||Gypframe G102 Retaining Channel|
|Horizontal joint||Glasroc F FireCase 20mm
Gypframe GA3 Steel Angle
|Core||Glasroc F FireCase 20mm|
|Board side 1||Layer 1: Glasroc F FireCase 15mm
Layer 2: Glasroc F FireCase 15mm
Layer 3: Glasroc F FireCase 15mm
|Screws side 1||Layer 1: British Gypsum Jack-Point Screws 35mm
Layer 2: British Gypsum Jack-Point Screws 41mm
Layer 3: British Gypsum Jack-Point Screws 60mm
|Stud||Gypframe 146 TI 90 Tabbed 'I' Stud|
|Abutment channel||Gypframe 146 TSC 90 Tabbed Starter Channel|
|Head channel||Gypframe 148 EDC 80 Extra Deep Flange Floor & Ceiling Channel|
|Fixing strap||Gypframe GFS1 Fixing Strap|
|Base channel||Gypframe 148 DC 60 Deep Flange Floor & Ceiling Channel|
This section should be read in conjunction with the Products list.
- Abutment Fixing: Gypframe starter channel suitably fixed wall at 600mm centres in two lines staggered by 300mm.
- Base Channel Fixing: Gypframe channel suitably fixed to floor at 600mm centres in two lines staggered by 300mm.
- Deflection Allowance: Vertical deflection only. To be determined by a Structural Engineer.
- Dropped Soffit: For principles of deflection head construction refer to detail ST‐129‐Z2L3‐07.
- Finishing Requirements: To achieve the specified performances, the system should be finished using either one of our Thistle or ThistlePro plasters, or Gyproc jointing products. See the product range guides on the British Gypsum website for more information.
- Fixing Strap: Used to support horizontal board joints in face layer of multiple layer board linings and enable board screw fixing at 300mm centres.
- Horizontal Joint: Horizontal board joints in core layer closed off by inserting steel angle between board joints and 122mm strip of core board fire stop with beads of sealant along both longer edges fixed to angle using three drywall screws.
- Loadbearing: No
- Maximum Height: The maximum heights quoted are limited by the fire state field of application or by limiting deflection of L/240 at 200 Pa, whichever is the lower of the two.
- Other Requirements: SpecSure® system performance warranty confirms that British Gypsum proprietary systems will perform as specified for the lifetime of the building. The SpecSure® warranty requires that all components are specified in full and constructed in accordance with British Gypsum’s installation guidance. For more details see the British Gypsum website. Always check with the design team before making any changes to the chosen specification, ensuring appropriate substantiation is sought to confirm that the solution still meets all required project performances.
- Retaining Channel: Retaining channels inserted between the face of the coreboard and the flange of the stud / starter channel.
- Screw: Board layers are fixed securely to Gypframe metal supports around the perimeter of the board and intermediate stud positions at maximum 300mm centres. External corners reduce fixings to 200mm. Drywall screws can be used for fixing boards to metal profiles with a thickness of 0.8mm or less (excluding 'I' studs). All joints staggered between layers. Fix working from the centre of each board. Position screws not less than 13mm from edges of boards. Set screw heads flush with plasterboard surface; do not break gypsum core.
- Sealant: Locate sealant at junctions with adjoining structure and other air paths. Apply as a continuous bead to clean, dry, dust-free surfaces, leaving no gaps. After application of sealant, bulk fill gaps between floor and underside of plasterboard using Gyproc jointing compound. For pressurised airshafts and service ducts apply a continuous bead of sealant leaving no gaps to all framing members at perimeter junctions with walls, floors and ceilings, air gaps around openings, and other potential air leakage points. To frame members prior to fitting core boards and around fire stops cloaking horizontal core board joints. To all metal framing around board perimeters of first layer boarding and board perimeters when fixing outer layer board.
- Stud Centres (mm): 600 mm
- Approx. Weight (kg/m2): 62 kg/m²
- Head Channel Fixing: Gypframe channel suitably fixed through fire stop in to soffit at 600mm centres in two lines staggered by 300mm.
Log in to access CAD .dwg files.
Log in and add a System Specification to a Project to access BIM files, Test Reports, and Technical Specification files.
Please add this Specification to a project and go to that Project to access the related Test Reports.
|Test report label||Test report name|
|Test report labelFire Resistance Test Report||Test report nameBTC 16887FA|
|Test report labelFire Height Test Report||Test report nameBTC 16887FA|
|Test report labelSound Insulation Test Report||Test report nameBG G306 A|
A unique warranty that confirms British Gypsum proprietary systems will perform as specified for the lifetime of the building.